The data center industry spoke, and ASHRAE listened. The society is no longer proposing the use of PUE to set data center efficiency standards in a new standard document that’s currently in the works.
ASHRAE drew criticism from some prominent industry voices last year after it released the first draft of standard 90.4, whose goal is to set energy efficiency standards specifically for data centers, recognizing that large stand-alone data centers need a special approach and cannot be lumped in with other building types as they currently are in standard 90.1.
Standard 90.4 is being created to work together with 90.1 and references a lot of definitions in the older standard, meant for all building types, except low-rise residential buildings.
ASHRAE doesn’t enforce compliance with its building standards, but they are a big deal because local building officials in the US use them extensively in building inspection and permitting.
PUE Gone from the Standard
The most controversial part of the first draft of 90.4, released for review and comment in February 2015, was its reliance on PUE, or Power Usage Effectiveness, as the data center energy efficiency metric.
Developed and promoted by The Green Grid, it is the industry’s most widely used (and most widely misused) metric, but the draft’s critics argued that using PUE in the ASHRAE standard would disadvantage colocation providers, whose facilities often run at partial load for the majority of their lifespan.
Put simply, the metric compares power consumed by IT to total power supplied to the facility. The bigger the portion of total power that doesn’t make it to IT equipment on the data center floor, the more inefficient the facility’s infrastructure is. Therefore, the more power IT equipment consumes, the better the overall PUE. If the success of your business relies to a great extent on having available capacity for more servers, that unused capacity will theoretically have negative impact on your PUE.
Second draft of 90.4, released last August, got rid of PUE, introducing instead two new efficiency metrics – Mechanical Load Component and Electrical Loss Component – but made PUE one of the alternative options for compliance.
The latest draft, released for review this January, gets rid of PUE altogether, replacing it in the alternative compliance section with a metric that combines MLC and PLC.
As an example, here’s how Design MLC (there’s Design MLC and Annualized MLC) is calculated:
More details on MLC and PLC in the draft itself, which is worth reviewing and commenting on as soon as possible if your job has anything to do with data center design and operation.
The point of the alternative compliance method is to give data center operators more flexibility. If the mechanical system doesn’t meet the required MLC level, but the electrical system is so efficient that it compensates for inefficiency of the mechanical system, they can use the combined metric to comply with the standard.
Cooling Upgrade Requirements Clarified
Another complaint was that the initial draft could be interpreted in a way that would force operators to upgrade existing cooling systems.
The new standard should apply only to new data centers or data center expansions. But, if a data center expansion is getting some or all cold air from a previously existing cooling system, should that cooling system be upgraded too? That wasn’t clear in the first draft, but the current draft specifies that older mechanical systems supplying air to a new portion of a data center don’t have to be upgraded.
Don Beaty: founder of the engineering firm DLB Associates. Beaty has spent many years on ASHRAE committees dedicated to developing data center standards.
Chris Crosby: co-founder and CEO of data center developer and provider Compass Datacenters. Crosby is a data center industry veteran who was part of the team that founded Digital Realty Trust, the world’s largest wholesale data center developer and provider.
Rich Miller: founder and former editor in chief of Data Center Knowledge. Miller is currently editor in chief at Data Center Frontier, which he also founded.
Join Don Beaty, Chris Crosby, Rich Miller, myself, and 1,300 of your peers at Data Center World Global 2016, March 14-18, in Las Vegas, NV, for a real-world, “get it done” approach to converging efficiency, resiliency and agility for data center leadership in the digital enterprise. More details on the Data Center World website.
Original article appeared here: ASHRAE Strikes PUE from Data Center Efficiency Standard Draft